Staticworx® ESD tile flooring is a solid vinyl product offering excellent static control performance.
Our ESD vinyl tile is an ideal choice for clean rooms, health care applications, electronics manufacturing, access floors, labs and tech spaces or anywhere static control is essential to your business or operation.
All Staticworx Ameriworx ESD vinyl tile meets ESD Association ( ESDA ) standards. Download complete independent consultant's ANSI/ESD S20.20-2014 certification of Staticworx conductive vinyl tile.
|SPECIFICATIONS||AMERIWORX® Series ESD Vinyl Tile
Made in USA
|Construction:||Precision milled vinyl tile of high density resin with a conductive carbon matrix.|
|Thickness:||1/8", 3.2 mm|
|Size:||12" x 12" stock
24" x 24" custom
36" x 36" custom
|Static Generation Comparison Less than 20 Volts per ESD STM 97.2||< 12 V|
(ASTM F 540):
|Static Load Limit
(Mod. ASTM F 970-00):
Meets ANSI/ESD S20.20
2.5 X 10E4 - 1.0 X10E6
Static Dissipative: 1.0 X 10 E6 - 1.0 X 10 E9 Per ANSI/ESD S7.1 - 2005
|Static Decay:||<0.01 seconds|
INDOOR AIR QUALITY INFORMATION
FloorScore® Indoor Air Quality Certified to SCS-EC10.3-2014 v3.0 Conforms to the CDPH/EHLB Standard Method v1.1-2010 (California Section 01350), effective January 1, 2012, for the school classroom and private office parameters when modeled as Flooring. Measured Concentration of Total Volatile Organic Compounds (TVOC): Less than/equal to 0.5 mg/m3(in compliance with CDPH/EHLB Standard Method v1.1-2010)
California Department of Health CDPH/EHLB/Standard Method Version 1.1, 2010 (Emission testing method for CA Specification 01350)
- CALGreen, CA Code of Regulations Title 24, Part II, 2010, Sections 4.504.4/5.504.4.6: Resilient Flooring Systems
- ANSI/ASHRAE/USGBC/IES Standard 189.1-2009, Section 188.8.131.52: Floor Covering Materials
- USGBC LEED CI, NC, Schools, 2009, IEQ Credit 4.3: LEM - Flooring Systems
- USGBC LEED for Healthcare, 2009 (Feb 2011), IEQ Credit 4: LEM, Group 3 - Flooring
- Collaborative for High Performance Schools (CHPS) rating system, 2009 Criteria EQ2.2.3: Flooring Systems
- Green Guide for Healthcare, V2.2, 2007, EQ Credit 4.3: LEM - Flooring Systems
Important Note: Static conductive flooring should never be used in emergency 911 communication applications or FAA flight control areas. Staticworx recommends Eclipse rubber and ShadowFX carpet tiles for these applications.
Note: To achieve maximum performance, all ESD vinyl tile requires the use of static control footwear in combination with the floor.
*For more complete AMERIWORX® Vinyl specifications, click here to download a PDF version
Maintenance and Cleaning Procedures for Ameriworx Tile:
Ameriworx® Vinyl Flooring Maintenance Guidelines
Ameriworx® Vinyl Post-Installation Maintenance Guidelines
Learn more about specifying antistatic flooring for applications requiring the control of unwanted electrostatic discharge by reading our article How To Specify Static-Free Floors in the September 2011 issue of The Construction Specifier Magazine.